- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 21 Oct 2017
New requirements for fire detection and alarm network systems IP 12 13
New requirements for fire detection and alarm network systems (IP 12/13) was written by Eman Mattie-Suleiman and published by BRE on 30 September 2013.
A fire detection and alarm systems (FDAS) typically consists of a processer unit, which receives signals from detection and activation functions such as smoke and heat detectors and activation of manual call points. After analysis of the incoming signals, the status of the system is indicated via the user interface and the appropriate outputs are initiated such as the activation of sounders/beacons, signals to the alarm receiving centre, or signals to activate protection devices such as extinguishing systems.
The development of FDAS components has been driven by new technology, the growth in microprocessor power at low prices, new legislative requirements and user specifications. Different types of FDAS are now available on the market and the selection of the appropriate system will depend on a number of factors including:
- Building size.
- Complexity of the action(s) to be taken due to a fire event within a building.
- Cost of the system and its installation.
This 12 page BRE information paper enables the specifiers and designers of fire detection and alarm systems to choose the most appropriate hard-wired network systems whilst maintaining compliance with the Construction Products Regulation (CPR) and BS 5839-1 (Fire detection and fire alarm systems for buildings. Code of practice for design, installation, commissioning and maintenance of systems in non-domestic premises). It also highlights the requirements for network systems which have been developed and incorporated within a Loss Prevention Standards (LPS) standard.
The contents of the information paper are:
- Background-Introduction of network systems.
- Reasons for networking fire detection and alarm systems.
- Current requirements for fire detection network systems.
- New fire detection and alarm system network requirements.
 Related articles on Designing Buildings Wiki
- Automatic fire detection and alarm systems, an introductory guide to components and systems BR 510.
- BRE articles on Designing Buildings Wiki.
- BRE Buzz articles on Designing Buildings Wiki.
- BRE Buzz.
- Building Research Establishment.
- Fire detection and alarm system.
- Fire detector.
- Heat alarm.
- Ionisation smoke alarm.
- Multi-sensor alarm.
- Optical smoke alarm.
- The causes of false fire alarms in buildings.
Featured articles and news
If events occur that cause the completion of the works to be delayed then these may be compensation events.
BSRIA's new Building MOTs Scheme is designed to provide guidance on the next steps after compliance.
At an ICE discussion, the focus was on delivering a Northern Infrastructure Strategy based on opportunity for all.
The Considerate Constructors Scheme officially launch the new Ultra Site status for contractors and supply chains.
The risk of specification errors in the cladding sector is "worryingly high" after Grenfell, according to major distributor.
Here is our outline work plan for a private sector design and build project.
BRE are to publish new guidance aimed at assuring buyers as to the merits of off-site construction methods.
Who are the various different stakeholders in development projects? Find out in our introductory article.
How a BRE office became the centre-piece for major biophilic design research.
A new interactive virtual experience allows visitors to explore ICE 200 exhibition from anywhere.