- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 13 Mar 2017
Initial commissioning case studies
Essentially, initial commissioning is just proof of capability, such as the ability of a mechanical ventilation system to deliver the required air volumes, or the heating system to provide the required heat output. Tests will include health and safety checks, and controls systems will be checked. Set-points will be fixed and recorded in the documentation.
Full-load commissioning may not be possible prior to occupation. Loads may not be available because of the time of year, or phased occupation may mean internal heat gains are absent. Ventilation systems working at full capacity might reveal noise or vibration problems, or the terminal units might create unpleasant draughts. As such problems may only emerge later, it raises the logic of having a graduated handover. See: Soft Landings for more information.
 Case studies: Carbon Trust's Low Carbon Building's Programme
All the buildings included in the Carbon Trust's Low Carbon Building's Programme (LCBP) were categorised as low-carbon buildings, in that they either had on-site renewable energy generation or some other technology that reduced carbon dioxide emissions. These technologies tended to be commissioned by a specialist - in most cases either the installer or manufacturer. Many manufacturers provided a commissioning checklist for their product. Once completed, the checklists were retained in the handover documentation.
While this was fine at the point of commissioning, problems tended to surface later. For example, some suppliers of low carbon technologies are based in continental Europe, which affected the speed of response to calls for advice, information or maintenance. Downtime suffered as a result. Standby boilers installed as back-up to biomass boilers often ran more often than was intended.
Some overseas firms employ local representatives to carry out commissioning. For example, while the biomass boiler serving the Riverside Dene estate was sourced from the Swiss company Schmid, all commissioning was carried out by Imperative Energy, Schmid's UK partners. By contrast, a ground-source heat pump at Edge Hill University was commissioned by the German supplier, which visited the site three times in order to ensure the installation was correctly set up.
Additional buildings are being added to the community heating scheme well after the initial commissioning activities have been completed. Instead of setting a strict commissioning schedule, the system is continuously monitored by Vital Energy, which is operating the system. Vital Energy has an experienced engineer who can adjust the system as required. This is essential in a residential community heating scheme, where patterns of occupation may vary.
Remote diagnostic/monitoring systems are increasingly common for technologies such as CHP plant and biomass boilers. Where available, they should be identified and included in the commissioning programme.
For its Canolfan Rheidol headquarters building near Aberystwyth, Ceredigion County Council had a knowledgeable internal facilities team who could understand the technologies. Similarly, at Pembrokeshire College the requirement for training was put into the contract, with the contractor required to submit a detailed programme of training to the client. The training was given to key personnel by the main contractor and specialist installers over two days, with sessions on the biomass boiler and BMS.
Training has to be given to the personnel who are actually going to operate the building. It's even better if the facilities team can be involved during the construction so they are fully up to speed at the point of handover.
Above: Canolfan Rheidol, the headquarters for Ceredigion County Council. The building is on a biomass district heating scheme. Initial problems with the biomass system saw heating defaulting to the back-up gas boilers.
This article originally appeared in Delta T Magazine May 2011, written by BRIA’s James Parker, where additional copyrighted images are included. It was posted here by --BSRIA 08:31, 26 November 2014 (UTC).
 Related articles on Designing Buildings Wiki
- Client commissioning.
- Commissioning documents.
- Commissioning notice.
- Commissioning plan.
- Commissioning planning.
- Commissioning v testing.
- Corrosion in heating and cooling systems.
- Handover to client.
- Migration strategy.
- Commissioning planning.
- Practical completion.
- Seasonal and continuous commissioning.
- Soft landings.
Featured articles and news
Which room is the most fun to design? Find out the 'Grand Designs' presenter's unusual choice in our interview.
Full suite of speakers are announced for this year's BSRIA Briefing event.
Book your place for the Architectural Technology Awards 2018.
There are many ways of classifying types of building. Have a look at our range of building articles.
BSRIA have launched the 'major update' of the go-to design framework guide for building services.
How to get results with building life cycle assessment.
Government publishes a prospectus inviting proposals for new 'garden communities'.
The Morandi motorway bridge in Genoa collapses during rainstorm while undergoing maintenance works.
'Developed design' is a phrase coined by the RIBA for their 2013 Plan of Work. But what does it actually mean?
New green paper published aiming to rebalance the relationship between landlords and residents and tackle stigma.
RIBA calls for a comprehensive ban on combustible materials.