- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 29 Mar 2019
Failure of metals
The implications and impact of metal failure in construction are significant, ranging from economic damage to possible injury and structural instability. Metal components fail for a wide range or reasons. Elements of which they are a component could be badly designed, or the metal components themselves could be poorly designed, fabricated or maintained, or they might be used outside of their intended purpose.
Metal failures can occur unexpectedly and so are often difficult to anticipate. It is important therefore that anticipated conditions are carefully modelled during the design process to pinpoint where potential failures may occur.
Where they do occur, metal failures should be subject to a systematic and detailed investigation to determine the cause and to identify avoidance measures for the future. Forensic engineering is capable of determining the root cause of metal failures with a great deal of accuracy. Unique identifiers are left by the various failure types which enable the exact nature of the failure to be identified.
This type of failure is caused when applied loads stress the metal beyond its ultimate strength. Failures can occur very rapidly, and are influenced by the material type, its heat treatment, and so on. Overload failures are generally categorised as:
- Ductile: The component stretches or bends to some degree before failure.
- Brittle: The component breaks with little or no distortion.
Metal components will have design specifications which identify the maximum load that is capable of being applied before failure occurs. Keeping the component loading levels well below the design specifications is the simplest and easiest way of avoiding this kind of failure.
It occurs when repeated or fluctuating loads are imposed that allow a small material failure to develop into a larger one, over a long period of time. A fatigue crack is allowed to gain a foothold, usually at a machine mark, corrosion pit, surface scratch or other surface imperfection. The beach markings indicate the direction of the crack as it progresses across the fracture face. Total failure occurs when the applied load cannot be carried by the unaffected area that remains.
 Stress corrosion cracking (SCC)
SCC is caused when three factors are in combination:
Laser peening is a remedial solution that can modify the surface of components and reduce the risks attached to operating in a corrosive environment imparting beneficial residual stresses in materials.
Fretting can occur when the surfaces of metal components slide against one another and generate abrasive compounds. As this motion continues, the abrasive components score the surface and cause a form of wear known as fretting.
Creep is a risk for metal components that are exposed to stresses at elevated temperatures. Deformation results from grain boundary sliding, a mechanism in which grains are displaced against each other at high temperatures.
Hydrogen embrittlement occurs as a result of exposure to hydrogen, for example, in the manufacture or processing of high-strength steels and titanium and aluminium alloys. It reduces the ductility and load-bearing capacity of affected materials, which can cause cracking or failure at below normal yield stresses.
For more information, see Hydrogen embrittlement.
 Related articles on Designing Buildings Wiki
- Defects in construction.
- Failure of cast iron beams.
- Forensic investigations: can we trust them?
- Guidance for construction quality management professionals: Structural Steelwork.
- Hydrogen embrittlement.
- Latent defects.
- Major cast metal components.
- Metal fabrication.
- Patent defects.
- Roofing defects.
- Stainless steel.
- Structural failures.
- Structural steelwork.
- Types of steel.
Featured articles and news
The Ocean Cleanup project
The various types of bond and when they are used.
It's vital the industry responds to proposals for reform of the safety regulatory system.
RSHP's Merano wins RIBA accolade.
How to differentiate between partial possession and early use.
Ofwat proposes £12 billion additional investment and £50 bill reductions.
Avoiding 'winner's curse' and other useful info.
Developing test methods for video flame/smoke detectors
Waiting for a new deal ...but will funding materialise?
Our servers have reached another milestone. Why not write an article and be seen by our 6.5 million users.
RSHP celebrates competition win in Paris.
All about approved inspectors.