- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 21 Nov 2017
Emergency lighting is installed in buildings in case of a mains power failure and provides sufficient illumination to allow occupants of the building to evacuate safely. Types of emergency lighting include; emergency exit signs, recessed fluorescent lights, powerful halogen emergency spotlights for larger spaces, emergency ceiling lights and downlights, and so on.
The Regulatory Reform (Fire Safety) Order 2005 requires that 'emergency routes and exits requiring illumination must be provided with emergency lighting of adequate intensity in the case of failure of their normal lighting.'
The requirement does not apply to domestic premises.
Approved document B defines emergency lighting as 'lighting provided for use when the supply to the normal lighting fails'. It defines escape lighting as 'that part of the emergency lighting which is provided to ensure that the escape route is illuminated at all material times.'
Approved document L defines emergency escape lighting as '......that part of emergency lighting that provides illumination for the safety of people leaving an area or attempting to terminate a dangerous process before leaving.'
In addition to the requirement to illuminate emergency routes and exits, open area lighting may be provided to allow occupants to reach an escape route, and where occupants are involved in activities that may present some danger if they are not completed, there may be high-risk task area lighting. There may also be standby lighting to allow occupants to continue with their normal activities in the event of a power failure.
Emergency lights are powered by back-up batteries. The lights detect when mains power has failed and immediately switch to using the back-up battery. The battery should be capable of powering the light, for a defined period, but as a means of conserving power, the light output may be reduced, sometimes to just 10% of the normal output.
The Fire Precautions (Workplace) Regulations 1997 and BS 5266 part 1 require that building owners test emergency lighting regularly and maintain them in proper working order. Light fittings have a green LED indicator which shows they are charged and functional.
There are three basic types of emergency light fitting:
This type of fitting is designed to operate as a normal light fitting, to be lit continuously and to be controlled along with the other lights in the area. However, if power fails the maintained emergency fitting will continue to operate at a lower light output level. This type of lighting is commonly used in public buildings such as theatres, cinemas and shopping centres.
This type of fitting is normally switched off, but is designed to switch on automatically in the event of a mains power failure. The batteries are continuously charged. These are typically fittings such as emergency exit signs which are not required as part of general lighting. They are commonly used in workplaces such as offices and factories, where there may be more occupant familiarity with the building and the escape routes.
Includes two lamps, one operating on a mains supply, and the other operating in the event of mains power failure from a battery source.
 Other categorisations
Fittings may be self-contained, with their own batteries, or may be powered from a central battery source.
They can have varying durations for which they are able to remain illuminated following a mains power failure, such as 1 hour, 2 hour, 3 hour and so on.
They may provide different levels of illumination. See below.
 Technical requirements
The specification for emergency lighting will depend on the area it is intended to illuminate.
 Open areas
A non-obstructed escape route must be lit during an emergency to a minimum of 1 lux. Emergency lighting isn’t required if the open area is less than 60 sq. m and isn’t part of a designated escape route. The exit doors for the emergency escape route must be fitted with signs or an emergency bulkhead light.
As stairwells provide increased levels of hazard than unobstructed spaces, they must be lit during an emergency to a minimum of 2 lux.
 Related articles on Designing Buildings Wiki
Featured articles and news
Dr Nicholas Falk, director of the URBED Trust, explains why metro cities are the future of urbanisation.
From next week, UK firms can bid for a share of a £12.5m fund to boost productivity, performance and quality.
A right to light generally refers to the right to receive sufficient light through an opening.
Interference and compatibility - the effects of electromagnetic fields in the workplace.
Important action is being taken to inspire young people to train as engineers.
A survey of Leicester’s historic buildings resulted in local listing being taken more seriously.
Demolition is the most high risk activity in the construction sector. Read our introductory article here.
BSRIA report on the domestic boiler market, with China recording the most 'dynamic market uptake'.
Do we really know everything important about the impacts of our infrastructure projects? And if we don’t, does it matter?
Former Chief executive Richard Howson blames government for being 'poor payers'.