- Project plans
- Project activities
- Legislation and standards
- Industry context
Last edited 18 Aug 2018
Earth to air heat exchangers
An earth-to-air heat exchanger draws ventilation supply air through buried ducts or tubes. As the temperature of the ground below 3m is practically constant, it substantially reduces ambient air temperature fluctuations. It therefore provides space conditioning throughout the year, with the incoming air being heated in the winter and cooled in the summer by means of earth coupling.
 System options
Systems can be driven by natural stack ventilation, but usually require mechanical ventilation. In some cases air is circulated via air handling units, allowing filtering and supplementary heating/cooling. A simple controller can be used to monitor inlet and outlet temperatures, as well as indoor air temperatures. Ground coupling ducts or tubes can be of plastic, concrete or clay – the material choice is of little consequence thermally due to the high thermal resistance of the ground.
Earth-to-air heat exchangers are suited to mechanically ventilated buildings with a moderate cooling demand, located in climates with a large temperature differential between summer and winter, and between day and night. Location of the ducts in sand or gravel below the water level, where there is moving ground water, gives the best performance, however, the presence of ground water involves extensive sealing precautions.
 Size and output
depth of 2m and separated by 1-2m to allow heat dissipation. The optimum air velocity is typically 2m/s.
Under constant load, the cooling capacity of the ground may become exhausted and, therefore, generally it is not possible to meet high loads. With high loads, two separate duct systems could be considered – one for use in the morning and one for use in the afternoon.
A bypass can be used to improve the performance of the system during periods when the ambient air temperature can meet the cooling requirements. In unoccupied periods when the ambient air temperature falls below the surface temperature in the ducts, night cooling can be used to pre-cool the system.
The ground temperature is based on ‘undisturbed’ conditions. When the ducts are installed beneath the building, or even within a built up area, this will be affected substantially. The effect that the duct has on the ground temperature also needs to be considered. Optimisation of the design requires a complete thermal simulation of the system.
Earth-to-air heat exchangers can be used on new buildings or refurbishments to provide free cooling in the summer and pre-heating of air in the winter. They have high capital costs, but over the life of the system can yield substantial savings.
This article was created by --Buro Happold 17 March 2013, based on a 2008 article in 'Patterns'.
 Find out more
 Related articles on Designing Buildings Wiki
- Coefficient of Performance CoP.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Geothermal energy.
- Geothermal pile foundations.
- Ground energy options
- Ground preconditioning of supply air.
- Ground source heat pumps.
- Renewable energy sources: how they work and what they deliver: Part 3: Electrically driven heat pumps DG 532 3.
- Thermal labyrinths.
Featured articles and news
BSRIA report suggest the European market will double to 415 million Euros by 2023.
Do you understand the different types of stone and which ones you should use where?
Why a wellbeing strategy is vital for property managers.
An ECA briefing for members about the commercial implications of leaving the EU.
A crucial moment on any project - and fraught with danger.
The performance gap from a Northern Ireland perspective.
Book review: Buildings of protestant nonconformity.
Design and testing for health and wellbeing - free download from BRE.
Retention in construction contracts.
Campaign for the reform of cash retentions.
The key points for the construction industry and BSRIA's response.