Earth to air heat exchangers
An earth-to-air heat exchanger draws ventilation supply air through buried ducts or tubes. As the temperature of the ground below 3m is practically constant, it substantially reduces ambient air temperature fluctuations. It therefore provides space conditioning throughout the year, with the incoming air being heated in the winter and cooled in the summer by means of earth coupling.
 System options
Systems can be driven by natural stack ventilation, but usually require mechanical ventilation. In some cases air is circulated via air handling units, allowing filtering and supplementary heating/cooling. A simple controller can be used to monitor inlet and outlet temperatures, as well as indoor air temperatures. Ground coupling ducts or tubes can be of plastic, concrete or clay – the material choice is of little consequence thermally due to the high thermal resistance of the ground.
Earth-to-air heat exchangers are suited to mechanically ventilated buildings with a moderate cooling demand, located in climates with a large temperature differential between summer and winter, and between day and night. Location of the ducts in sand or gravel below the water level, where there is moving ground water, gives the best performance, however, the presence of ground water involves extensive sealing precautions.
 Size and output
The optimum pipe length is a function of pipe diameter and air velocity. Small pipe diameters of between 200 and 300mm are thermally more efficient. Pipes should be buried at a minimum
depth of 2m and separated by 1-2m to allow heat dissipation. The optimum air velocity is typically 2m/s.
Under constant load, the cooling capacity of the ground may become exhausted and, therefore, generally it is not possible to meet high loads. With high loads, two separate duct systems could be considered – one for use in the morning and one for use in the afternoon.
A bypass can be used to improve the performance of the system during periods when the ambient air temperature can meet the cooling requirements. In unoccupied periods when the ambient air temperature falls below the surface temperature in the ducts, night cooling can be used to pre-cool the system.
The ground temperature is based on ‘undisturbed’ conditions. When the ducts are installed beneath the building, or even within a built up area, this will be affected substantially. The effect that the duct has on the ground temperature also needs to be considered. Optimisation of the design requires a complete thermal simulation of the system.
Earth-to-air heat exchangers can be used on new buildings or refurbishments to provide free cooling in the summer and pre-heating of air in the winter. They have high capital costs, but over the life of the system can yield substantial savings.
This article was created by --Buro Happold 17 March 2013, based on a 2008 article in 'Patterns'.
 Related articles on Designing Buildings Wiki
Featured articles and news
In the week of the momentous Heathrow decision, we look back at the development and design of T5.
BSRIA’s flagship event will address performance and wellbeing beyond compliance.
Young Architects and Developers Alliance launched to build the relationship between the two disciplines.
BS 8536-2:2016 Design and construction: Code of practice for asset management (Linear and geographical infrastructure).
Paying for off-site goods or materials can be useful, but it puts the client at risk.
People power can be transformative if properly informed and inspired.
ZHA win competition to build an Urban Heritage Administration Centre in Saudi Arabia.
Leaps, not steps, are needed to avoid a ticking time bomb, say BRE in response to Farmer Review.
A multi-purpose hall in France covered in a translucent orange membrane.
Winning designs revealed for a rock formation-influenced residential complex in Rennes.
An article explaining the techniques, regulations and environmental impacts of carbon capture and storage.
Watch one of the first documentaries by the acclaimed Adam Curtis, examining the substandard system building of the 1960s.