Convection in buildings
Convection is the movement of a fluid, such as air. It is a combination of advection and diffusion:
- Advection is the large-scale motion of a fluid in currents.
- Diffusion is the small-scale movement of particles of fluid from areas of higher concentration to areas of lower concentration.
Convective air movement in buildings is very important to:
- Help moderate internal temperatures.
- Reduce the accumulation of moisture, odours and other gases that can build up during occupied periods.
- Improve the comfort of occupants.
Natural air movement can be either wind driven, or buoyancy driven.
- Wind-driven air movement is caused by a difference in pressure between the inside and outside of the building caused by wind.
- Buoyancy-driven air movement is caused by the tendency for warm air to expand, and so become less dense and more buoyant, rising through the general air mass. Conversely cool air contracts, becoming more dense and less buoyant and falling through the air mass. This can create circulating currents of rising and falling air.
Convection is also a heat transfer mechanism (along with radiation, conduction and phase change). Convective heat transfer in buildings results from the movement of air of different temperatures and can be used to maintain internal comfort, either through heat exchange between the air and the internal surfaces of a building, or by heat exchange with sources of heating or cooling, sometimes driven by fans.
Convection can be noticeable above hot radiators where warm air rises, or next to windows where there may be a cold downdraught. These effects can be exploited at a larger scale in systems such as displacement ventilation, and in passive building design through effects such as the stack effect.
Accurately predicting the movement of air within building is extremely complicated and can require the use of computational fluid dynamics (CFD) modelling software. CFD works by dividing a body of air (or any other fluid) into a series of cells that represent the fluid volume surrounded by surfaces and openings that represent the enclosure. The software will then simulate the flow of air from each cell to those surrounding it, and the exchange of heat between the boundary surfaces and the cells adjacent to them. After a series of iterations, the model will come to a steady state that represents the actual air velocities and distribution of temperatures expected to be found within the space. See CFD for more information.
 Related articles on Designing Buildings Wiki
- Building fabric.
- Heat transfer.
- Heat transfer coefficient.
- Long wave infra red radiation.
- Mass transfer.
- Mean radiant temperature.
- Natural ventilation.
- Phase change materials.
- Solar gain.
- Solar radiation.
- Thermal bridge.
- Thermal optical properties.
- Thermal mass.
- U value.
Featured articles and news
Sadiq Khan publishes a new development strategy for the capital.
In the week of the momentous Heathrow decision, we look back at the development and design of T5.
BSRIA’s flagship event will address performance and wellbeing beyond compliance.
Young Architects and Developers Alliance launched to build the relationship between the two disciplines.
BS 8536-2:2016 Design and construction: Code of practice for asset management (Linear and geographical infrastructure).
Paying for off-site goods or materials can be useful, but it puts the client at risk.
People power can be transformative if properly informed and inspired.
ZHA win competition to build an Urban Heritage Administration Centre in Saudi Arabia.
Leaps, not steps, are needed to avoid a ticking time bomb, say BRE in response to Farmer Review.
A multi-purpose hall in France covered in a translucent orange membrane.
Winning designs revealed for a rock formation-influenced residential complex in Rennes.
An article explaining the techniques, regulations and environmental impacts of carbon capture and storage.
Watch one of the first documentaries by the acclaimed Adam Curtis, examining the substandard system building of the 1960s.