Computational fluid dynamics for buildings
This is important as it allows designers to investigate the temperature distribution and air movement within buildings before they are built, allowing them to test options and select the most effective solutions.
CFD can be a useful tool for modelling:
- The comfort of occupants.
- The distribution of environmental conditions within a space.
- The effectiveness of building services (such as the positioning of air inlets and extracts or radiators).
- The consequences of fire (such as the spread of heat and smoke).
- The effectiveness of natural ventilation (such as the stack effect)
- The build up of heat in specialist spaces such as server rooms.
- The positioning of sensors. For example in a tall space, the temperature at the top might be very different to the temperature at the bottom. This can be important when positioning temperature sensors that feed back to the building management system. Otherwise, heating and cooling might be operating unnecessarily.
- The impact of a new building on air movement around a site.
Simulations might be run for a number of different scenarios, testing the behaviour of a space under different levels of occupancy, different climatic conditions, in different modes of building services operation or, with different openings between spaces and so on. This can build up an overall picture of how a building is likely to behave under normal operating conditions as well as during unusual or extreme conditions.
CFD works by dividing a space into a grid containing a large number of 'cells'. The grid of cells is surrounded by boundaries that simulate the surfaces and openings that enclose the space. The temperature of the boundaries, the air movement at openings, and the air temperature within the cells is then set to a starting condition which it is hoped is close to those that might be expected to be found within the space. This might include a boundary model that predicts boundary conditions, based on climatic and materials data. The closer this starting condition is to the final position predicted by the model, the faster the model will run.
The software will then simulate the flow of air from each cell to those surrounding it, and the exchange of heat between the boundary surfaces and the cells adjacent to them. After a series of iterations, the model will come to a steady state that represents the actual air velocities and distribution of temperatures expected to be found within the space.
Increasingly, CFD software is able to interact with other models, such as:
- Boundary models.
- Climatic models.
- Building services models.
- Energy consumption and CO2 generation models.
- Radiant models.
- Daylighting and lighting models.
- CAD and BIM software.
CFD can be a very useful tool in the right hands, and output graphics are very persuasive and seductive. However results are highly dependent on the knowledge of the person setting up the model and interpreting the results. This is an increasing concern as CFD software becomes more straight-forward to use and so is more easily operated by people with little understanding of the mathematical model that underpins it.
If the input information is wrong, the output information will be as well.CFD is no substitute for common sense.
An important consideration in developing a CFD model is the generation of the grid of cells. The greater the number of cells, the more accurate the simulation will be, but the longer the model will take to run. In some parts of a space, using a large cell size may not have a significant impact on the results, however in sensitive areas, for example around complex boundaries or where there might be a large temperature difference between a boundary surface and the air next to it, it is important that cells are as small as is computationally practical. For example a very small cell size (a fine grid mesh) is necessary to properly simulate the downdraft that can be experienced next to a cold window. If such a downdraft is not simulated, the heat exchange between the window and the space it encloses will be underestimated.
In spaces where the surfaces enclosing the space are non-cartesian (ie they are curved, or at an angle rather than purely horizontal or vertical) it is important that the grid is body-fitted (ie that it follows the contours of the surfaces) rather than cartesian (in a series of steps), otherwise air velocity at the surface will be underestimated and so heat transfer between the space and its enclosing surfaces will be underestimated. This is particularly important where there is a large temperature difference between the surface and the air adjacent to it.
Where CFD is being used to predict user comfort within a space, it is important that both air temperature and radiant temperature are considered. CFD in itself only models air temperature and air velocity, however, around half of the contribution to our thermal comfort within buildings is dependent on radiant heat transfer, ie the temperature of the surfaces around us. Some CFD software is able to include radiant influences on the temperatures that will be felt by occupants.
Analysis of the influence of a roof on track level wind speeds for the London 2012 Olympic Stadium.
--Gregor Harvie 07:56, 9 June 2014 (BST)
 Related articles on Designing Buildings Wiki
- Conventions for calculating linear thermal transmittance and temperature factors.
- Dynamic thermal modelling of closed loop geothermal heat pump systems.
- Energy targets.
- Heating degree days.
- Heat transfer.
- Mass transfer.
- Mechanical ventilation.
- Natural ventilation.
- Passive building design.
- The design of temporary structures and wind adjacent to tall buildings.
- The thermal behaviour of spaces enclosed by fabric membranes (Thesis).
- Thermal behaviour of architectural fabric structures.
- Thermal comfort.
 External references
- An Investigation into the thermal behaviour of spaces enclosed by fabric membranes, Gregor Harvie, 1996.
- Performance evaluation of CFD codes in building energy and environmental analysis, Pedro Dinis Gaspar, Rui F. Barroca and R.A. Pitarma, 2003
- CFD online.
- Application of Computational Fluid Dynamics in Building Design: Aspects and Trends, Zhiqiang Zhai, 2006.
Featured articles and news
The origins, evolution and future of Level 3 BIM.
For new and returning Urban Design students, check out our article list divided up into the modules you'll be studying.
Report states that health of urban dwellers could be significantly improved by rethinking transport design.
The Kremlin, the centre of Russian power, includes some of the country's finest architecture.
Report launched outlining steps for a national infrastructure system that is efficient, sustainable, and delivers until 2050.
A review of Justin Bere's concise and well-presented introductory guide to Passive House.
This article describes in detail the tender process for a typical commercial construction contract.
What is energy storage, what are the different types and what is its future?
MAD Architects reveal their designs for a state-of-the-art concert hall in Beijing.
Take a look at BIG's designs for two twisting towers in New York City.
'The filing cabinet' which was labelled one of the best British buildings of the 21st century.