Active thermal mass in buildings
To help develop this article, click ‘Edit this article’ above.
The term ‘thermal mass’ describes the ability of a material to absorb, store and release heat energy. Thermal mass can be used to even out variations in internal and external conditions, absorbing heat as temperatures rise and releasing it as they fall. In building design, this can useful for evening out and delaying extremes in thermal conditions, stabilising the internal environment and so reducing or eliminating the demand for building services systems. It can be beneficial both during the summer and the winter.
Thermal mass is often considered to be a passive component of environmental design, with heat transfer between the internal air of the building interior and the thermal mass by ‘natural’ convection. However, it can be difficult to achieve close temperature control with passive thermal mass, and large quantities of thermal mass can be required.
The term ‘active thermal mass’ refers to the controlled absorption and release of heat energy from thermal mass. This active control can be used to maximise heat transfer between thermal mass and internal spaces and to better tune the absorption and release of heat to heating and cooling demands.
Active thermal mass systems are generally air-based or fluid-based systems.
- Air-based systems operate by drawing ventilation air past the thermal mass at low velocity, to maximise the heat transfer with the air. This can be achieved by using the hollow core in pre-cast concrete slabs as a ventilation duct, or using the void created by raised floors as a supply plenum. Air-based systems can be used to regulate the temperature of the thermal mass during occupied periods and for night-time purging.
- Fluid-based systems typically pump water through pipes embedded in the floor slab (similar to underfloor heating piping) to moderate the temperature of the thermal mass. Water has a greater cooling potential than air, however, in this case, ventilation must be provided separately. The water temperature is generally maintained at above 14°C to avoid condensation, and it can also be used to provide heating in the winter.
Building management systems can be used to control active thermal mass systems based on internal and external temperatures, the temperature of the mass, the occupancy pattern of the building and any heating, ventilation and air conditioning (HVAC) systems.
 Related articles on Designing Buildings Wiki
Featured articles and news
Watch one of the first documentaries by the acclaimed Adam Curtis, examining the substandard system building of the 1960s.
Take a look at the tech start-up that could transform construction design and communication.
This house in Barcelona uses an innovative new facade tiling system to blend into the landscape.
The origins, evolution and future of Level 3 BIM.
For new and returning Urban Design students, check out our article list divided up into the modules you'll be studying.
Report states that health of urban dwellers could be significantly improved by rethinking transport design.
The Kremlin, the centre of Russian power, includes some of the country's finest architecture.
Report launched outlining steps for a national infrastructure system that is efficient, sustainable, and delivers until 2050.
A review of Justin Bere's concise and well-presented introductory guide to Passive House.
This article describes in detail the tender process for a typical commercial construction contract.
'The filing cabinet' which was labelled one of the best British buildings of the 21st century.